7.14.050 PLUMBING FACILITIES AND FIXTURE REQUIREMENTS.
Chapter 5 Plumbing Facilities and Fixture Requirements is amended as follows:
(a) Section 505.4 Water heating facilities is amended as follows:
Water heating facilities shall be properly installed, maintained and capable of providing an adequate amount of water to be drawn at every required sink, lavatory, bathtub, shower and laundry facility at a minimum temperature of 110° F (43°C). A gas-burning water heater shall not be located in any bathroom, toilet room, bedroom or other occupied room normally kept closed, unless the installation complies with Title 23 Buildings and Construction. An approved combination temperature and pressure-relief valve discharge pipe shall be properly installed and maintained on water heaters.